Payment & Shipping Terms:
|Shell:||Alum-zink Galvanized Steel Plate||Power Nature:||380V/3P/50HZ|
|Cooling Coils:||T2 De-acidified 99.99% Purity Copper Coils||Water Basin:||304 SS Steel Plate|
|Wind Louvre:||Anti-corrosion; Sun Sheltering; Drift Elimination||Header Pipe:||Galvanized Steel With Stainless Liner|
|Fan:||Motor Grade: IP55; Insulation: F; Alum-alloy Blades; Axial Flow||Spare Parts:||Depending On The Circumstances|
|Electrical Components:||Schneider Brand|
copper tube cooler,
coppercounterflow cooling tower
Copper Tube Cooling tower EVAPCO copper cooler T2 de-acidified 99.99% Cooling tower BAC copper tube cooling tower:
2.2 Advantages for cooling towers
1) Closed loop
Preventing the impurities into the system to block the cooling tubes, soft water is adopted to avoid overheating caused by scaling to the water pipes.
2) Automatic temperature control
Automatic start/stop spraying system to achieve effective control on the temperature of cycled cooling water, the temperature of the cooling water can be controlled below 40 ℃. With this function, the water & energy cost is reduced to the lowest point with intelligent control to the number of working fans and start & stop of spray pump.
3) No need of water pool and cooling tower
Low cost, small space occupancy, easy installation and move with the welder.
4) Automatic digital display of temperature control
Energy efficient and user friendly.
5) Cooling system structure
Galvanized iron beam.
6) High efficiency heat exchange
Four side air inlet louvers supply sufficient amount of wind blowing through cooling coils taking most of the heat away, which effect is strengthened via spray cooling water running through the cooling coils.
|Nominal Flow Rate||300 m3/h|
|Work Flow Rate||235 m3/h|
|Wind Flow Rate||2×120000m3/h|
|Spray Pump Power||7.5kw|
|Spray Water Flow Rate||172m3/h|
|Spray Pump Raise||9.6m|
|Inlet/Outlet Diameter||DN 200mm|
|Makeup Connection||DN40 (Please specify adopted screw standards)|
|Bleed Line Diameter||DN50 (Please specify adopted screw standards)|
Contact Person: Peter.Zeng