Payment & Shipping Terms:
|Shell:||Alum-zink Galvanized Steel Plate (S.Korea) δ=2mm||Cooling Coil:||Hot Dip Galvanized Seamless Carbon Steel Coils∮=25mm δ=2.0mm|
|Power Supply:||380v /3P/50HZ (415v/3P/50HZ)||Refrigerant Liquid:||Ammonia /R717|
|Water Basin:||304 SS Steel Plate||Motor Grade:||IP55 Insulation: F|
|Electrical Components:||Schneider Brand||Water Eliminator:||Anti-corrosion Sun Sheltering Drift Elimination|
|Spray Pump:||Cast Iron(SIEMENS)|
bac evaporative condenser,
evapco evaporative condenser
Ammonia Condenser Industrial Cooling Equipment NH3 Evaporative condenser R717 Evaporative Condenser R22 Evapo
High temperature gaseous refrigerant agent and hence the
refrigerant agent becomes liquid.inside it has a water
distribution system, condensing coils,wet deck ,dehydrator and
so on. Outside it has a water circulating pump , a propeller fan
on the top of condensing coil. The propeller fan strengthens
the flow of the air and causes negative pressure inside.
when the condenser runs,the cooling water is pumped and
then sprayed by water distribution system On the surface of
condensing coil equably to form a thin layer of water film.
2.1.2 Water Cooling:
The high –temperature steam of refrigerant agent enters from the top of condensing coil and then the cooled liquid refrigerant agent is discharged from the bottom of the condenseing coil .during this process,high temperature refrigerant agent exchanges the heat with the water and air outside the coil and increases the the effect of heat exchange with the help of wind .after aborbing the heat of refrigerant agent .some water turns into steam and is discharged by fan .meanwhile,the moisture in the
Air is collected by dehydrator to basin.and the ungasified cooling water flows into wet deck and its heat is taken away by the airflow .the cooled water converges in the basin to be used circularly by the pump.
In addition,there is a ball cock in the basin .when the water is consumed to a certain point the ball cock
Will automatically open to replenish the cooling water.
2.2 Evaporative Condensers Configuration and Technical Performance
The evaporative condensers main machine consists of shell, cooling coils, air discharge system, spray system, drift Eliminator and water basin etc.
|Evaporative Condenser||Cooling Coil||Spec.||High –quality hot dip galvanized seamless carbon steel Coils∮=25mm δ=2.0mm|
|Shell||Upper Shell||Alum-zink galvanized steel plate (S.Korea) δ=2mm|
|Water Basin||Alum-zink galvanized steel plate (S.Korea) δ=2mm|
|Fan System||Fan||Motor grade: IP55; Insulation: F; Alum-alloy blades; Axial Flow|
|Water Eliminator||Anti-corrosion PVC|
|Wind Louvre||Anti-corrosion; Sun sheltering; drift elimination|
|Spray System||Spray Pump||Cast iron|
|Spray Nozzles||ABS basket nozzles of umbrella style|
|The Fastening Pieces||High quality Grade 304 SS Steel Plate|
Drainage valve 1 unit,
Hand tools 1 set;
Sealing tapes 1 set;
Float bulb 1 unit;
Basin filter 1 unit;
|Power Nature : 380V/3P/50HZ|
Contact Person: Peter.Zeng